Complete PLC and HMI software update ready for your computers!
All the announcements with the new stuff are compressed together with the software in the same .zip
So you don’t need to download separatelly.
Our intention with this blog is to publish small examples and tips that are useful for the programmer, yet not enough important to appear in the newsletter.
If anybody would like to collaborate with it, don’t hesitate to send your post to email@example.com. I’ll be pleased to upload it.
The posts need to be written in English and be as illustrated as possible, either with images or videos.
May 4, 2019 at 8:30 am
Do you have available Delta HMI – PLC programming manual.
August 28, 2015 at 7:38 am
Problem solved. Have to tick “Hold” option in Options -> Alarm Setup. Default this option is OFF.
August 20, 2015 at 1:04 pm
Please install PATCH to version 2.04.04.09.zip
June 11, 2015 at 1:25 pm
i am using DOP-B10E615 for my new project. every thing was going perfect suddenly following ERROR appearing after code compile,
“memory not enough in panel SDRAM”
July 10, 2015 at 10:56 am
have the same issue:
“memory not enough in panel sdram”
it shows when i add alarm history table and try to compile
program version (build): DOPSoft 2.00.04.04
October 24, 2013 at 1:01 pm
how can we connect Delta HMI with PC for data logging in Excel without using e-server software?
waiting for reply.
July 17, 2013 at 8:45 pm
Greetings of the day!
I need your help on an issue that involves HMI and Printer setting.
My problem is i need to use a laser printer with my application and the mentioned models of laser printers for HP and Epson are out-dated and I am not able to complete the commissioning job. Kidly tell me whether can we use any other printer of the same series with the HMI? will it work?
SUch as in DOPSoft HP laserjet 1022N is given and it is not available but its successor Laserjet 1020 is available. so will it work with the HMI?
July 18, 2013 at 8:44 am
Look for a printer with pictbridge protocol (http://en.wikipedia.org/wiki/PictBridge), and you’ll be able to print.
March 9, 2013 at 6:39 pm
I have a problem with the program WPLSoft V2.33. When I compile a window aparce saying “tempoary compiler can not create some files”. Also I can not close the program another window appears saying “Can not create file”. Can you help me solve this?
February 11, 2013 at 5:26 pm
Stepper Motor programming
Greetings of the day!
I am using one stepper motor for a horizontal job application.
I have never used any stepper before. I wants to know about commands that can DPLSY and DPLSR commands be used for stepper motors, and how to control its speed?
Kindly resolve my problem.
February 1, 2013 at 7:28 am
Please! Add text data type from historical data table.