November 2, 2016 at 6:35 pm
driver for indusoft
April 23, 2016 at 11:23 am
I have analogue input 1v to 10v and i need to connect with a plc delta and make a program that can read this input and transfer it to timer .
If i have 1v it’s meaning for the program 3s and every time I increase the voltage the timer must increase with it.
So can you help me and to tell me how to make it ?
January 12, 2017 at 7:01 am
You can design a simple program for it. i will give you basic structure for it.
Use delta ADC plc then from it you will get a value suppose 12345 which proportional to your input analog voltage then you store that value in D register suppose at address D200 then do a multiplication our division on it to get timer value as you need then store it at other place suppose D210. then when you use timmer intruction u can use direct this D210 value. E.g. ” TMR T1 D210 “… in Delta PLC 10 = 1 sec.
If need sample program on it don’t hesitate to mail me i will give you sample program for it.
May 22, 2014 at 8:01 am
We having problem to access modbus address in C2000 Series, we wan to communicate C2000 Series to our Scada system under modbus protocol. But we only can accessed parameter P0.0-P0.61 (parameter drive) equal to modbus address 40001 to 40062, others parameter we couldn’t accessed it. However we have try using modbud poll software to access it, but the problem having same. Please advice if we have missing in the setting paramater of the drive
Fill in your details below or click an icon to log in:
You are commenting using your WordPress.com account. ( Log Out / Change )
You are commenting using your Twitter account. ( Log Out / Change )
You are commenting using your Facebook account. ( Log Out / Change )
You are commenting using your Google+ account. ( Log Out / Change )
Connecting to %s
Notify me of new comments via email.
Notify me of new posts via email.
Enter your email address to subscribe to this blog and receive notifications of new posts by email.
Join 1,419 other followers
Blog at WordPress.com.